Earthleakage Circuit Breaker (ELCB) RCD of High Quality
|FOB Price:||US $21 / Piece|
|Min. Order:||500 Pieces|
|Min. Order||FOB Price|
|500 Pieces||US $21/ Piece|
|Payment Terms:||L/C, T/T|
- Model NO.: FNL1-800
- Operation: Manual Type
- Arc-extinguishing Medium: Air
- Structure: ELCB
- Type: Circuit Breaker
- Certification: ISO9001-2000, CB, CCC
- Rated Current: up to 800A
- Pole: 2p, 3p, 4p
- Trademark: FUNELEC or OEM
- Specification: 100A, 125A, 160A, 180A, 200A, 225A, 250A
- HS Code: 85362000
- Breaking Capacity: Low Voltage Circuit Breakers
- Speed: Normal Type Circuit Breaker
- Installation: Fixed
- Poles Number: 3
- Function: RCCB
- Frequency: 50Hz
- Multiple Release: Selectable
- Rated Working Voltage: 400V
- Transport Package: Carton
- Origin: China
Standard export packing or According to customer's demand ;According to customer"s quantity
about 30 days
FNL11 series rediual current circuit breaker,is mainly applied to the distribution circuit of AC 50Hz,rated working voltage is 400V,rated current up to 800A for providing protection indirectly and prevent the fire caused by the fault gounding current,and it also can be used for power distribution and circuit protetion against overload and short-circuit,it also works for transfering circuit and starting motor unfrequently.
This production also is suitable for isolation.
This production conforms to the standard of IEC60947-2 and GB14048.2.
Normal operational conditions and installation conditions
3.1 Temperater: no higher than +40ºC,and no lower than -5ºC,and the day average temperature no higher than +35ºC.
3.2 Altitude: no higher than 2000m
3.3 The relative humidity: no more than 50%,when temperature is +40ºC.The product can withstand higher humidity under lower temperature,for instance,when it at +20ºC,the production can withstand 90% relative humidity.
The condensation that happened because of temperature changes should be taken care.
And Installation location should have no exploresion danger, and no gas and conductive dust which can cause corrosion and insulation damage.
3.4 Class of pollution: 3 Calss
3.5 Maximum install inclined angle: 5°,it should be installed at the place without obvious impact and weather-influence.
3.6 Main circuit installation type:III
Auxiliary circuit and control circuit installation type:II
3.7 External magneticfield of installation location should be not exceed than 5 times of earth magnetic field.
3.8 Installation electromagnetic environment:B type
For more details and information,Please feel free to contact us.
|Model||Rated current In A||Rated operate voltage V||Rated short-circuit breaking capacity||Rated residual action current In(mA)||Rated residual no-action current In(mA)||Arc distance mm|