Earthleakage Circuit Breaker (ELCB) of Dz15L-100-4901 63amagnetic Circuit Breaker
- Model NO.: DZ15L
- Operation: Manual Type
- Arc-extinguishing Medium: Air
- Structure: ELCB
- Type: Circuit Breaker
- Certification: CE, CCC
- Specification: CCC, CE
- HS Code: 85362000
- Breaking Capacity: Low Voltage Circuit Breakers
- Speed: Normal Type Circuit Breaker
- Installation: Fixed
- Poles Number: 4
- Function: Magnetic Circuit Breaker
- Trademark: FUNELEC
- Origin: China
DZ15LE series intelligent type earthleakage circuit breaker, is applied to distribution power-net of frequency 50Hz, Rated operate voltage 220V or 380V, Rated current up to 100A. And it provides indirect protection, it is also used to prevent the fire dange which cause by grounding fault becasue of equipment insolation damage.
And it is applied to distribute electric power and protect circuit band power-supply device against overload and short-circuit, and it also works for circuit unfrequently transfering and motor unfrequently starting.
This production conforms to the standard of IEC60947-2 and GB14048.2.
Normal operational conditions and installation conditions
3.1 Temperature: No higher than +40º C, and no lower than -5º C, and the day average temperature no higher than +35º C.
3.2 Altitude: No higher than 2000m
3.3 The relative humidity: No more than 50%, when temperature is +40º C. The product can withstand higher humidity under lower temperature, for instance, when it at +20º C, the production can withstand 90% relative humidity.
The condensation that happened because of temperature changes should be taken care.
And Installation location should have no exploresion danger, and no gas and conductive dust which can cause corrosion and insulation damage.
3.4 Class of pollution: 3 Calss
3.5 Maximum install inclined angle: 5° , it should be installed at the place without obvious impact and weather-influence. Upper terminal for power-supply side, Lower terminal for loading side.
3.6 Installation type: III
3.7 Installation electromagnetic environment: B type
3.8 External magneticfield of installation location should be exceed than 5 times of earth magnetic field.
For more details and information, please contact us with no hesitate